Wooden Drum or Customerized
Inspection Certificate of Fumigation available
Shipped in 10 days after payment
185mm2 and 300mm2 MV Amour Cable Wire with KEMA Certificate
Conductor: Circular stranded copper conductor, conforms to IEC 60228 class 2
Inner Covering: PVC
Armour: Galvanized Steel Amour Wire or tape
Sheath: PVC type ST2 to IEC 60502, black
Note: Insulation color as per standards or customer requirement
Used for Power transmission and distribution line with voltage rated at 35kv and below. Compared with PVC Insulated Power cable, XLPE power cable boasts not only characteristics of excellent electricity, mechanism , heat and aging- resistant, environment stress-resistant and chemical corrosion resistant, but also simple structure, light weight,
no restriction by laying drop, and high temperature allowance for long term working.
For Layling indoors and outdoors. Able to bear certain traction during installation, but not external mechanical forces. Standards
International: IEC 60502, IEC 60228
China: GB/T 12706.1-2008
Other standards such as BS,DIN and ICEA upon request
Rated voltage: 2-35 kV
Max. Conductor Temp.: normal (90°C), short circuit no more than 5 s (160°C when section-area below 300mm2, 140°C when section-area above 300mm2)
Min.Ambient Temp.:The cable shall be pre heated if the ambient temperature is below 0°C
Min. Bending Radius: single core cable 20(d+D)±5%
Multi-core cable 15(d+D)±5%
1. Long term working temperature is up to 90℃.
2. The highest conductor temperature is not more than 250℃.(lasting time not over 5 seconds.)
3. Laying temperature not less than 0℃ and the drop height is out of consideration.
4. The cable with chemical stability, anti acid, anti alkali, and oil, anti organic solvent, not easy to be burning.
5. Easy for installation, easy beading and light.
6.Bending ratio as follow
CE, RoHS, CCC, KEMA and more others at request
4 Table of the voltage, cores and cross-section
The cable with Category A rated voltage is used in the situation requiring not over 1 min. of grounding fault lasting time. For the cable with Category B rated voltage, the grounding fault lasting time normally is not over 1 hour, max. lasting time is not over 8 hours, annual ground fault lasting time altogether should not be over 125 hours, Category C includes all the system expect Category A and B.